Built in 1968, the College of Education has been serving students for 52 years. With an aging HVAC system, the team discovered that while the distribution between two chillers was nearly identical, both pumps could only supply approximately 60% of the design flow at 60Hz. The team performed system measurements and final adjustments to the hydronic distribution system.
Location: Pocatello, Idaho
Owner: Idaho State Division of Public Works
MEP Designer: Musgrove Engineering